What should I be aware of when operating MY4 General-purpose Relays AC100V Relay from a distance?
The distance depends on the type and installation conditions of the cable. Wiring power supplies over a long distance in parallel with power lines may cause reset failure due to voltage generated at both sides of the Relays from float capacitance in the wires when the coil input power supplies are OFF. If reset failure occurs, connect bleeder resistors to both sides of the coil.
Guideline for Cable Length Limits
|Preconditions||Must-operate voltage of up to 90% of rated voltage allowed|
(Formula is applicable up to a cable length of 3 km.)
|Example: For MY4 Relays||100 VAC, 60 Hz, MY4 with CW Cable|
Answer: Value exceeds 3,000 m so there is no problem with cables up to 3 km.
New Latching Levers for Circuit Checking Added to Our Best-selling MY General-purpose Relays
Power-switching Compact General-purpose Relays
Compact, Slim-profile SSRs with Heat Sinks. Solid State Contactors for Three-phase Heaters Reduced Installation Work with DIN Track Mounting.