What are the conditions for detecting disconnection for G3PX-2EHN-CT Power Controllers that detect disconnection for multiple heaters?
The disconnection detection conditions are listed below.
1. The load current must be 1 A min.
2. The CT detection current must be 30% or higher of the rated maximum load current.
Note:Increase the number of CT turns if the CT detection current is 30% or less.
3. Up to five heaters can be connected (20% multiple heater disconnection detection characteristics)
Care must be taken because the following phases are not detected by heater disconnection detection.
New Latching Levers for Circuit Checking Added to Our Best-selling MY General-purpose Relays
Power-switching Compact General-purpose Relays
Compact, Slim-profile SSRs with Heat Sinks. Solid State Contactors for Three-phase Heaters Reduced Installation Work with DIN Track Mounting.