What is the maximum distance for operating MY4 DC24V General-purpose Relays?
The distance depends on the type and installation conditions of the cable. Both ends of the Relays coil must measure at least 90% of the rated coil voltage to operate without problems. It is essential to check this beforehand.
Reference Information: Guide to Limits of Cable Lengths
|Preconditions||Must-operate voltage of up to 90% of rated voltage allowed|
|Example: For MY4 Relays||24 VDC MY4 with CVV Cable|
Answer: The cable needs to be within approx. 4.2 km.
New Latching Levers for Circuit Checking Added to Our Best-selling MY General-purpose Relays
Power-switching Compact General-purpose Relays
Compact, Slim-profile SSRs with Heat Sinks. Solid State Contactors for Three-phase Heaters Reduced Installation Work with DIN Track Mounting.