|12 to 24 VDC (Allowable voltage fluctuation range: 10 to 30 VDC)
|0 to 1 MΩ variable
Note: The adjuster (ADJUST) on the top of the Sensor Amplifier sets the resistance for
detection within the setting range. It is factory-set to the upper limit. (Normally, the
K7L can be used with the adjuster at this setting.)
|Detection signal: 10 VDC max., 200 ms
Detection time: 10 s max.
Recovery: Operation is recovered by resetting the power supply.
||105% min. of operate resistance
|NPN open-collector transistor output with 100 mA at 30 VDC max. for both liquid leakage
detection and disconnection detection.
Note: If the rightmost pin of the DIP switch on the side of the Sensor Amplifier is set
to thedown position, the output turns ON when liquid is detected; if it is set to the
up position, the output turns OFF when liquid is detected.
||10 to 150 Hz, 0.1-mm single amplitude with 15-m/s2 acceleration for 8 minutes
10 times each in X, Y, and Z directions
||150 m/s2 3 times each in six directions on 3 axes
||Wiring cable, Sensing Band: Total: 400 m max.
Note: These values are possible on the condition that a completely insulated 3-conductor
VCT cable with a thickness of 0.75 mm2 and a dielectric strength of 600 V is
used together with the Liquid Sensing Band specified by OMRON. (A 0.2-mm2 cable can also be used.)
||Screwdriver for ADJUST