The Relay does not operate even when voltage is applied. Why is this?
The following causes are probable.
Ultrasonic cleaning or applying an overvoltage may cause the coil to become disconnected.
2.Insufficient Coil Voltage
Check the voltage being applied to the coil. The Relay will not operate if the voltage is lower than the must-operate voltage.
3.Incorrect Polarity of Applied Voltage
A Relay equipped with a diode that absorbs coil counter-electromotive force will not operate properly if the positive and negative voltages applied to the coil are connected incorrectly.
New Latching Levers for Circuit Checking Added to Our Best-selling MY General-purpose Relays
Power-switching Compact General-purpose Relays
Compact, Slim-profile SSRs with Heat Sinks. Solid State Contactors for Three-phase Heaters Reduced Installation Work with DIN Track Mounting.